Self -sufficient installation
At what point does the UV-C system have to be installed in the drinking water cycle?
A UV-C disinfection system is always the last link in a water treatment chain, since the path to the withdrawal point should be kept as low as possible. Water filters in particular offer ideal conditions for settlement by bacteria. The freshly disinfected water would therefore germinate again if it would continue through the drinking water cycle after going through the UV-C system. Printing boilers should always be installed in front of the UV-C systems.
When do I need a life of life?
A service life monitoring is recommended for all users who do not permanently let the system switch on. A change of the lamp is recommended every 10,000 hours, since the manufacturer also does not guarantee the performance, i.e. the amount of UV-C radiation dose required for safe disinfection.
Does the system automatically switch on the water flow?
The UV system should be permanently switched on for various technical reasons:
1.) The UV system needs about 1 minute to achieve full performance.
2.) When igniting the lamp, as much energy is required as for operation over two hours.
3.) Each on and off cycle is at the expense of the service life.
How do I know which UV-C system is the right one for me?
The correct dimensioning of the systems is not based on the maximum daily consumption but the expected maximum point of time and is therefore dependent on the performance of the pump.
What should be considered when installing 12V DC and 24V DC systems?
It should be noted that no power supplies with powdered voltage are used, which means that the system can suffer irreparable damage.
Can the system be operated with photovoltaic panels?
Yes, that is possible. However, the use of a battery is always recommended to ignite the lamp. In addition, a solar controller should always be used.
Do you recommend fuel germination?
No, we advise flow reactors, as the maximum distance between the water to disinfect and the UV-C lamp is precisely defined. A tank collision system can only ensure a complete disinfection if it has a previously calculated revolution. In addition, flow reactors are much more efficient.